Volume 23, Number 11—November 2017
CME ACTIVITY - Synopsis
Legionnaires’ Disease Outbreaks and Cooling Towers, New York City, New York, USA
Highlight and copy the desired format.
|EID||Fitzhenry R, Weiss D, Cimini D, Balter S, Boyd C, Alleyne L, et al. Legionnaires’ Disease Outbreaks and Cooling Towers, New York City, New York, USA. Emerg Infect Dis. 2017;23(11):1776. https://dx.doi.org/10.3201/eid2311.161584|
|AMA||Fitzhenry R, Weiss D, Cimini D, et al. Legionnaires’ Disease Outbreaks and Cooling Towers, New York City, New York, USA. Emerging Infectious Diseases. 2017;23(11):1776. doi:10.3201/eid2311.161584.|
|APA||Fitzhenry, R., Weiss, D., Cimini, D., Balter, S., Boyd, C., Alleyne, L....Varma, J. K. (2017). Legionnaires’ Disease Outbreaks and Cooling Towers, New York City, New York, USA. Emerging Infectious Diseases, 23(11), 1776. https://dx.doi.org/10.3201/eid2311.161584.|
The incidence of Legionnaires’ disease in the United States has been increasing since 2000. Outbreaks and clusters are associated with decorative, recreational, domestic, and industrial water systems, with the largest outbreaks being caused by cooling towers. Since 2006, 6 community-associated Legionnaires’ disease outbreaks have occurred in New York City, resulting in 213 cases and 18 deaths. Three outbreaks occurred in 2015, including the largest on record (138 cases). Three outbreaks were linked to cooling towers by molecular comparison of human and environmental Legionella isolates, and the sources for the other 3 outbreaks were undetermined. The evolution of investigation methods and lessons learned from these outbreaks prompted enactment of a new comprehensive law governing the operation and maintenance of New York City cooling towers. Ongoing surveillance and program evaluation will determine if enforcement of the new cooling tower law reduces Legionnaires’ disease incidence in New York City.
Legionnaires’ disease (LD) is a pneumonia associated with human-made water systems and is classified as nosocomial (≈10% of cases), travel-related (≈20% of cases), or community-acquired (≈70% of cases) (1,2). LD is caused by bacteria from the genus Legionella, with Legionella pneumophila serogroup 1 (Lp1) being detected in up to 80% of cases (3). The incidence of LD has increased ≈4-fold in the United States since 2000 and ≈3-fold in Europe since 1995 (4,5). The reasons for this increase are unknown but might be partly a result of increase awareness of LD and the consequent increased testing for LD. LD outbreaks account for 4%–11% of cases; the remainder (i.e., those without a determined source of exposure) are classified as sporadic (3,4). In the United States, 62% of LD cases occur during June–October (6), a period of generally warm weather when commercial air conditioning systems, including those with cooling towers (CTs), are in operation. An estimated 28% of sporadic LD cases may be caused by CT emissions (7).
The first LD outbreak ever detected was linked to a Philadelphia hotel CT in 1976 (8), and since then many of the largest LD outbreaks have also been associated with CTs (9–14). Detection of LD outbreaks is made difficult by the standard medical practice of treating community-acquired pneumonia without performing diagnostic testing (15). When Legionella is suspected, the urine antigen test provides a rapid result but might miss 26% of cases (16). This test only detects Lp1 and does not enable comparisons with environmental isolates (16). Legionella is a fastidious organism that requires specialized media and handling to culture. Respiratory cultures obtained after the start of antimicrobial drug use are less likely to grow; therefore, underdiagnosis and underreporting of LD cases is suspected (6). In addition, outbreaks of LD associated with CTs probably have gone undetected or, owing to the infrequency of obtaining clinical isolates, have been detected but not linked to a suspected CT.
In 2015, two LD outbreaks occurred in the New York City borough (county) of the Bronx, 1 of which was the largest ever in New York City and the second largest community outbreak in US history. Both outbreaks were linked to CTs by molecular characterization of clinical and environmental isolates. This prompted enactment of comprehensive legislation to regulate and inspect CTs to prevent LD outbreaks (17). We describe the evolution of community LD cluster detection and investigation, through the review of 6 LD outbreaks in New York City during 2006–2015, and the recent legislation enacted to control this environmental hazard.
LD has been a reportable condition to the New York City Department of Health and Mental Hygiene (DOHMH) since 1994. Every case is investigated, by chart abstraction and patient or proxy interview using standardized questionnaires, to determine whether the exposure could be associated with a healthcare facility (nosocomial), another type of building (e.g., a correctional facility, group home, hotel, shelter, residence, or workplace), or travel. Cases not belonging to these 3 categories are considered sporadic unless a link in space or time is recognized. LD cluster detection methods using surveillance data changed during the study period; during 2006–2013, the historical limits method (18) alone was used, and during 2013–2015, the historical limits method was modified to reduce bias (19). This method compares LD cases in the last 4-week period with data from the preceding 5 years and was applied at 3 geographic resolutions (citywide, borough, and neighborhood).
In addition, analyses using building identifiers (BINs) were added in January 2013 to identify LD events of public health concern. The BIN is a unique number assigned to every building in New York City, matched to patient address, and compared with a list of healthcare and other congregate facilities (20). The prospective space-time permutation scan statistic (SaTScan) was added in February 2014 and is used to detect LD clustering using either the home or work address that occurs within a flexible time window (21,22).
We defined a community outbreak of LD as cases meeting the Council of State and Territorial Epidemiologists definition (23) that were not associated with a healthcare facility or residential building and occurred in close space and time, as defined by either a markedly elevated incidence in >1 US postal code (ZIP code) area or by >1 cluster detection systems. Assignment of patients to outbreaks was defined by residential ZIP code area, work ZIP code area, and locations visited during the incubation period, as elicited during patient interviews. To identify community outbreaks, we reviewed DOHMH LD investigation reports, related files, and surveillance data for 2006–2015. The following outbreak characteristics were summarized: borough where the outbreak occurred, ZIP code areas in the outbreak zone, onset dates of cases, number of cases, LD incidence in outbreak zone compared with the rest of New York City (using intercensal population estimate for each outbreak year by ZIP code area), number of deaths, the proportion of patients who were culture-positive for Legionella, environmental test results, link between environmental and clinical isolates, intervals from detection of the outbreak to environmental source decontamination, and whether an outbreak source was found.
Environmental sample Legionella testing was conducted by the New York State Department of Health Wadsworth Center (WC), the DOMHH Public Health Laboratory (PHL), and independent contractors. Criteria used to classify positive environmental results differed by laboratory. WC and PHL considered any culture growth as positive, whereas independent contractors used various CFU thresholds to define positive results (24,25). Culture and pulsed-field gel electrophoresis (PFGE) were performed by PHL, and real-time PCR (rPCR) and whole-genome sequencing (WGS) were performed by WC. Remediation was recommended whenever Legionella species known to be a risk to human health were identified. The study was determined to be public health surveillance and did not undergo institutional board review. Analyses were conducted using SAS version 9.2 (SAS Institute Inc., Cary, NC, USA) and SPSS version 22.0 (IBM Corp., Armonk, NY, USA).
During January 1, 2006–December 31, 2015, a total of 2,262 confirmed LD cases were reported in New York City residents. Six community-associated LD outbreaks, comprising 213 total cases, 207 of which were in New York City residents (9.7% of all New York City cases), occurred during the study period (Technical Appendix Figure). Three outbreaks and 84% (174/207) of outbreak-associated cases occurred in Bronx residents. Cultures were positive for Legionella spp. for 14.5% (30/207) of New York City resident outbreak-associated cases (all Lp1) and 6.3% (130/2,055) of New York City resident non–outbreak-associated cases (90 Lp1, 2 L. pneumophila 3 [Lp3], 4 L. pneumophila 4 [Lp4], 3 L. pneumophila 5 [Lp5], 1 L. pneumophila 6 [Lp6], 3 L. micdadei, and 27 L. pneumophila of an undetermined serogroup).
Outbreak 1 was recognized in the spring of 2006, when an epidemiologist (D.C.) noticed that several LD cases occurred in residents of a large apartment complex (>100 buildings). Twenty-nine cases occurred in the outbreak zone, consisting of 5 ZIP code areas. LD incidence in the outbreak zone during June–October 2006 was 9.7 cases/100,000 persons compared with 1.1/100,000 for the rest of New York City (Table 1). Interviews of patients failed to identify a common exposure in >35% of respondents. No patients were culture-positive for Legionella, and no environmental sampling was conducted at the time. Four additional LD cases occurred in the outbreak zone in a 3-week period of May–June 2007. Environmental sampling was performed on 2 supermarkets (a mister and a CT), a department store CT, and a decorative fountain. The department store CT was culture-positive for Lp5 and a supermarket CT for Lp3. No source for the original outbreak or subsequent cases was determined.
The only community outbreak of LD detected in the borough of Manhattan occurred in the summer of 2008 (outbreak 2). An epidemiologist (D.C.) identified 7 cases clustered in space and time, and all but 1 patient was either a resident of federally subsidized (n = 2) or supportive housing for formerly homeless persons (n = 4). Two buildings were associated with 2 cases each. The LD incidence in the 3-ZIP code outbreak zone was 9.8/100,000 compared with 0.4/100,000 for the rest of New York City. Potable and hot water systems in 3 buildings, an irrigation system, a supermarket misting system, and 2 supermarket CTs were tested for Legionella. L. pneumophila serogroup 1 was isolated from a supportive housing building, and L. anisa from another residential building, both from the hot water systems. Testing of the supermarket CTs identified Lp6 in 1 and L. bozemanii in the other. No clinical Legionella cultures were obtained, and no definitive source of the outbreak was identified.
In the winter of 2014–2015, outbreak 3 was detected by the historical limits method, which signaled for the Bronx and was subsequently focused by a BIN analysis signal that occurred 29 days later. The cases were associated with a large apartment complex that was unique in that it had its own electricity-generating power plant that used a CT. Eight LD cases occurred over 3 months for an outbreak zone (single ZIP code area) incidence of 18.8/100,000, whereas the rest of New York City had an LD incidence of 0.5/100,000. Of note, 2 previous LD cases had occurred in this apartment complex during 2012–2013; these are not included in outbreak or rate calculation.
The outbreak marked DOHMH’s first use of rPCR to screen potential environmental sources. Four sites were sampled: the power plant CT, a mall CT, apartment building potable water, and water from a grocery store mister. Both Lp1 and Lp6 were identified in multiple water samples from the power plant CT by rPCR (29/30 samples) and culture (27/30 samples). The mall CT was positive for Lp6 by rPCR (7/10 samples) and culture (1/7 samples). No Lp1 was cultured from the potable water samples from the apartment complex; however, a consultant environmental service found L. anisa (2 samples from the same apartment). Samples from the supermarket mister were negative by rPCR and were not cultured. One patient isolate of Lp1 was recovered and was shown by PFGE to be indistinguishable from an isolate from the power plant CT. The power plant CT was remediated 40 days later and identified by PFGE as the source 53 days after the outbreak was first recognized (Table 2).
Outbreak 4 occurred in the spring of 2015 in a residential–commercial area in Queens. SaTScan analysis identified a cluster of 4 LD cases. The investigation included 3 LD cases in residents of 3 separate buildings of a public housing complex and 2 cases in residents of a nearby assisted-living residential building. The remaining case-patient residences were dispersed around the commercial center. Several CTs were identified in the outbreak zone, and, after visual inspection, environmental sampling was conducted at 1 CT and the residential buildings. All of the potable hot water samples from buildings in the public housing complex tested positive by rPCR and culture for Lp2. Potable water samples from the assisted-living facility were negative by rPCR and culture. The CT was positive for Lp1 by rPCR and culture. Although no patient had Legionella infection confirmed by culture, 4 were positive from sputum samples by rPCR for Lp1. Because no molecular comparison of environmental and human Legionella isolates was possible, a definitive source of the outbreak was not identified.
The 2 Bronx LD outbreaks in 2015 included the largest outbreak in New York City (outbreak 5) and 1 in an area of the Bronx with a high density of CTs (outbreak 6). Outbreak 5 was detected by SaTScan in July and was defined by 7 ZIP codes areas (108/138 cases). Outbreak-associated cases were also found in all New York City boroughs, surrounding non–New York City counties, and in visitors from 3 other states. The incidence in the outbreak zone was highest of all the outbreaks at 25.7/100,000. The corresponding incidence in the rest of New York City was 0.6/100,000. A combined city and state effort identified 55 CTs in the outbreak zone. CTs were screened by rPCR for the presence of Legionella, and those that were positive for Lp1 were cultured. Twenty-two CTs were found by rPCR to have Lp1, and 14 were Lp1 culture-positive. Twenty-three (21%) of the 108 outbreak zone resident case-patients were culture-positive for Lp1, and the isolates were indistinguishable by PFGE and WGS to an isolate obtained from a hotel CT. No human isolate matched to another CT. The hotel CT was remediated 14 days later and identified by WGS as the outbreak source 26 days after the outbreak was recognized (Table 2).
Outbreak 6 was recognized in a section of the Bronx several miles from outbreak 5 after the latter had ended. Two cases were identified by an epidemiologist (R.S.) who recognized that a workplace of a case-patient and residence of another case-patient were on the same city block. SaTScan signaled 2 days later, identifying 10 cases in the cluster, and a total of 15 cases were included in the outbreak (Table 1). DOHMH was in the process of compiling a registry of CTs at the time and identified a high concentration in the outbreak zone (64 registered CTs). Four patient isolates grew Lp1 and were indistinguishable by PFGE and WGS from the isolate obtained from a workplace CT. Fifty CTs were screened for Lp1 by rPCR; 12 were positive, and 8 subsequently found to be culture-positive. The workplace CT was remediated 4 days later and identified as the outbreak source by WGS 21 days after the outbreak was recognized (Table 2).
The ability of DOHMH to detect and respond to community LD clusters has evolved over time. Improvements to the cadre of cluster detection tools has given DOHMH the confidence that that even small LD clusters will be detected, as in outbreak 4. Only 2 outbreaks were detected in the first 8 years of the study period, before many of the cluster detection methods were implemented or improved, whereas 4 were detected in the past 2 years, all of which signaled by 1 or more of the cluster detection systems. Cluster detection systems have shown great utility in detecting LD increases, but they are not without cost. Although we now recognize and respond to smaller LD clusters, additional investigation resources are required. After outbreak 6, case-patient work addresses were added to SaTScan, and a new daily proximity analysis, able to identify 2 or more cases occurring within 0.2 miles and 30 days of each other, was implemented in January 2016.
The ability to identify and test CTs during community outbreaks of LD also has evolved. When clusters of cases could not be linked to a building’s water system, investigators used “shoe leather epidemiology” to identify other possible sources. Decorative fountains, supermarket misters, visible CTs, and other potential sources were discovered by walking through neighborhoods and interviewing area residents. Beginning in 2015, CTs were identified based on a list of buildings that had applied for tax credits from decreased sewer use, and a New York City Department of Buildings CT list was populated from building construction permits. However, as was made clear from outbreaks 5 and 6, these lists were incomplete. The creation of a CT registry would facilitate identification of potential sources during a suspected community LD outbreak; however, the paucity of clinical cultures for environmental source comparison remains a limitation. The use of rPCR became routine in 2015 and has allowed DOHMH to rapidly screen a large number of potential sources to identify colonized CTs and request immediate remediation. For the outbreaks in which an environmental source was successfully identified, the time elapsed from the beginning of the investigation to source remediation decreased from 40 to 4 days, and the time required to identify the source decreased from 53 to 21 days. We attribute the decrease to several factors, including improved cluster detection, laboratory capacity, identification of CTs, and the experience gained from investigations involving teams of epidemiologists, laboratorians, and environmental health engineers.
DOHMH routinely communicates information about seasonal and emerging diseases to the medical community through an email listserv that includes all licensed physicians and other healthcare providers who have voluntarily subscribed. Repeated communications and media coverage during the study period regarding LD, particularly in the Bronx, likely sensitized the medical community to test patients with pneumonia for LD, as shown by the more than doubling of Legionella isolates obtained in outbreak-associated cases.
Although large outbreaks of LD are rare in the United States, public health officials struggle with identifying sources for the bulk of LD cases classified as sporadic. The focus has been on CTs because of their ubiquitous presence and direct discharge of potentially Legionella contaminated mist into the atmosphere. In New York City, 75% of the 5,886 registered CTs are located in the borough of Manhattan, but the Bronx has the second fewest (288 CTs [5%]). The concentration of CTs does not appear to predict whether or where an LD outbreak will occur. Other factors, such as CT design, maintenance, and elevation will need to be evaluated. We note, for example, rooftop CTs are, on average, at higher elevations in Manhattan than in the Bronx. The median elevation of CTs in Manhattan is 14 floors high, with 50% of the CTs located 7–46 floors high. In comparison, the median CT elevation in the Bronx is only 4 stories high, with 50% of the buildings being 2–8 stories. Higher elevation of CTs in Manhattan might present a lower risk for disease transmission, a result of greater particle dispersion, evaporation, or bacterial death; alternatively, the diffusion of contaminated mist from CTs at higher elevations might render outbreaks more difficult to detect.
Poverty probably contributes to the burden of LD because of patient susceptibility to infection, delayed access to medical care, and the maintenance of CTs, all of which play a role in LD outbreaks (26,27). The Bronx is fourth largest of the New York City boroughs by population, third by population density, and has the highest proportion of residents living in poverty (28–30). In poorer neighborhoods, the prevalences of concurrent conditions (e.g., diabetes and HIV) and smoking are elevated (31–33). In addition, building owners in poorer neighborhoods might lack the fiscal resources to hire staff or access training related to CT maintenance and implement a water safety plan for their CT.
Only 3 community-associated outbreaks, all within the last 2 years of the study period and in the Bronx, were successfully linked to a CT. In the 3 outbreaks for which no link was made, clinical isolates were not obtained. Because DOHMH does not receive negative Legionella culture reports, we are unable to assess how well our guidance is followed or the culture success rate. These factors remain challenges to LD source identification, control, and prevention efforts. When the first outbreak in this series occurred, no centralized registry of CTs existed. In August 2015, the New York City Council enacted a law requiring the registration, inspection, maintenance, and annual certification of CTs and other aerosol-producing engineering devices with rules promulgated by DOHMH (17). The rules require the creation of CT maintenance plans with routine monitoring of water quality (pH, biocide residual, and conductivity), weekly heterotrophic plate counts, weekly inspections of equipment by maintenance staff, and Legionella culture at least every 90 days during CT operational periods. On the basis of monitoring and sample results, specific minimum corrective actions must be made to control risk for Legionella amplification.
Many countries, including the United Kingdom and 9 other nations in Europe, have enacted legislation to register and regulate CTs, but no standard approach exists, and few countries perform active oversight of compliance (34). In the absence of oversight, compliance with regulations is often low, despite established industry standards, such as those issued by the American Society of Heating, Refrigerating, and Air-Conditioning Engineers and the Cooling Technology Institute (35,36). In New York City, unannounced inspections and financial penalties are expected to improve compliance. After the new law’s enactment, during May 9, 2016–May 31, 2017, DOHMH had inspected 3,909 (79%) of registered CT systems. Samples from 46 systems, comprising 1 or more CTs, were found with Legionella exceeding 1,000 CFU/mL. Remediation in all instances was performed in accordance with the new regulations. In the absence of the regulations, it is likely that no samples would have been collected and tested for Legionella. DOHMH would have been unaware of the potential hazards, and remediation would not have occurred.
New York City is a densely populated metropolis with infrastructure that varies from individual homes to skyscrapers. Our experience with LD investigations might not be typical of other jurisdictions, and generalizing conclusions from a series of 6 outbreaks is difficult. Because the Legionella urinary antigen test primarily detects Lp1, outbreaks caused by other strains might have occurred and were missed. However, the ubiquitous nature of Legionella in the environment and the rising incidence of LD nationally highlight the urgent need to shift from relying on the alarm bell of human disease to primary prevention strategies designed to limit Legionella colonization and dispersal from human-made aerosol-generating devices. New York City’s new CT regulations will provide a test case to evaluate whether strict CT maintenance reduces exposure to Legionella and reverses trends in LD incidence and outbreaks.
Dr. Fitzhenry is an epidemiologist with the New York City Department of Health and Mental Hygiene, Bureau of Communicable Disease. His research interests focus on waterborne disease. Dr. Weiss is the Director of Surveillance with the New York City Department of Health and Mental Hygiene, Bureau of Communicable Disease. His research interests are the epidemiology of invasive bacterial infections.
We thank Marcelle Layton, Sharon Greene, Erin Andrews, and James Hadler for their review of the manuscript. We also thank the Department of Health and Mental Hygiene Public Health Laboratory, Bureau of Communicable Disease, Bureau Environmental Sciences and Engineering, and the New York State Department of Health Wadsworth Center Laboratory for their contributions to Legionnaires’ disease outbreak investigations.
R.F. and D.W. conceived the study, wrote the manuscript, had full access to all of the data in the study and take responsibility for the integrity of the data and the accuracy of the data analysis and interpretation. D.C., S.B., C.B., L.A., R.S., A.E., Y.L., I.R., T.P., A.K., P.L. contributed to the investigations reported by collecting, analyzing and interpreting the data. All authors read and approved the final version to be published and had input in revising the manuscript for intellectual content and style.
This work was supported by New York City Tax Levy and Epidemiology and Laboratory Capacity grants from the US Centers for Disease Control and Prevention.
- World Health Organization. Legionella and the prevention of legionellosis [cited 2016 Aug 1]. http://www.who.int/water_sanitation_health/emerging/legionella.pdf
- Centers for Disease Control and Prevention. Surveillance for travel-associated Legionnaires disease—United States, 2005–2006. MMWR Morb Mortal Wkly Rep. 2007;56:1261–3.https://www.ncbi.nlm.nih.gov/entrez/query.fcgi?cmd=Retrieve&db=PubMed&list_uids=18059257&dopt=Abstract
- Fields BS, Benson RF, Besser RE. Legionella and Legionnaires’ disease: 25 years of investigation. Clin Microbiol Rev. 2002;15:506–26.
- Garrison LE, Kunz JM, Cooley LA, Moore MR, Lucas C, Schrag S, et al. Vital Signs: deficiencies in environmental control identified in outbreaks of Legionnaires’ disease—North America, 2000–2014. MMWR Morb Mortal Wkly Rep. 2016;65:576–84.
- European Centre for Disease Prevention and Control. Legionnaires’ disease in Europe, 2013 [cited 2016 Aug 1]. http://ecdc.europa.eu/en/publications/Publications/legionnaires-disease-2015.pdf
- Centers for Disease Control and Prevention (CDC). Legionellosis --- United States, 2000-2009. MMWR Morb Mortal Wkly Rep. 2011;60:1083–6.
- Bhopal RS, Fallon RJ, Buist EC, Black RJ, Urquhart JD. Proximity of the home to a cooling tower and risk of non-outbreak Legionnaires’ disease. BMJ. 1991;302:378–83.
- Fraser DW, Tsai TR, Orenstein W, Parkin WE, Beecham HJ, Sharrar RG, et al. Legionnaires’ disease: description of an epidemic of pneumonia. N Engl J Med. 1977;297:1189–97.
- García-Fulgueiras A, Navarro C, Fenoll D, García J, González-Diego P, Jiménez-Buñuales T, et al. Legionnaires’ disease outbreak in Murcia, Spain. Emerg Infect Dis. 2003;9:915–21.
- Shivaji T, Sousa Pinto C, San-Bento A, Oliveira Serra LA, Valente J, Machado J, et al. A large community outbreak of Legionnaires disease in Vila Franca de Xira, Portugal, October to November 2014. Euro Surveill. 2014;19:20991.
- Lévesque S, Plante PL, Mendis N, Cantin P, Marchand G, Charest H, et al. Genomic characterization of a large outbreak of Legionella pneumophila serogroup 1 strains in Quebec City, 2012. PLoS One. 2014;9:e103852.
- Bennett E, Ashton M, Calvert N, Chaloner J, Cheesbrough J, Egan J, et al. Barrow-in-Furness: a large community legionellosis outbreak in the UK. Epidemiol Infect. 2014;142:1763–77.
- Castilla J, Barricarte A, Aldaz J, García Cenoz M, Ferrer T, Pelaz C, et al. A large Legionnaires’ disease outbreak in Pamplona, Spain: early detection, rapid control and no case fatality. Epidemiol Infect. 2008;136:823–32.
- Walser SM, Gerstner DG, Brenner B, Höller C, Liebl B, Herr CE. Assessing the environmental health relevance of cooling towers—a systematic review of legionellosis outbreaks. Int J Hyg Environ Health. 2014;217:145–54.
- Hollenbeck B, Dupont I, Mermel LA. How often is a work-up for Legionella pursued in patients with pneumonia? a retrospective study. BMC Infect Dis. 2011;11:237.
- Shimada T, Noguchi Y, Jackson JL, Miyashita J, Hayashino Y, Kamiya T, et al. Systematic review and metaanalysis: urinary antigen tests for Legionellosis. Chest. 2009;136:1576–85.
- New York City Rules. Cooling towers: new Chapter 8 in Title 24 of the Rules of the City of New York to establish rules for maintenance of cooling towers [cited 2016 Aug 1]. http://rules.cityofnewyork.us/content/cooling-towers-new-chapter-8-title-24-rules-city-new-york-establish-rules-maintenance
- Stroup DF, Williamson GD, Herndon JL, Karon JM. Detection of aberrations in the occurrence of notifiable diseases surveillance data. Stat Med. 1989;8:323–9, discussion 331–2.
- Levin-Rector A, Wilson EL, Fine AD, Greene SK. Refining historical limits method to improve disease cluster detection, New York City, New York, USA. Emerg Infect Dis. 2015;21:265–72.
- Levin-Rector A, Nivin B, Yeung A, Fine AD, Greene SK. Building-level analyses to prospectively detect influenza outbreaks in long-term care facilities: New York City, 2013-2014. Am J Infect Control. 2015;43:839–43.
- Kulldorff M, Heffernan R, Hartman J, Assunção R, Mostashari F. A space-time permutation scan statistic for disease outbreak detection. PLoS Med. 2005;2:e59.
- Greene SK, Peterson ER, Kapell D, Fine AD, Kulldorff M. Daily reportable disease spatiotemporal cluster detection, New York City, New York, USA, 2014–2015. Emerg Infect Dis. 2016;22:1808–12.
- Council of State and Territorial Epidemiologists. Position statement 09-ID-45. Public health reporting and national notification for legionellosis [cited 2016 Aug 1]. http://c.ymcdn.com/sites/www.cste.org/resource/resmgr/PS/09-ID-45.pdf
- Nazarian EJ, Bopp DJ, Saylors A, Limberger RJ, Musser KA. Design and implementation of a protocol for the detection of Legionella in clinical and environmental samples. Diagn Microbiol Infect Dis. 2008;62:125–32.
- Mérault N, Rusniok C, Jarraud S, Gomez-Valero L, Cazalet C, Marin M, et al.; DELPH-I Study Group. Specific real-time PCR for simultaneous detection and identification of Legionella pneumophila serogroup 1 in water and clinical samples. Appl Environ Microbiol. 2011;77:1708–17.
- Farnham A, Alleyne L, Cimini D, Balter S. Legionnaires’ disease incidence and risk factors, New York, New York, USA, 2002-2011. Emerg Infect Dis. 2014;20:1795–802.
- Greene SK, Levin-Rector A, Hadler JL, Fine AD. Disparities in reportable communicable disease incidence by census tract-level poverty, New York City, 2006–2013. Am J Public Health. 2015;105:e27–34.
- New York City Office of City Planning. Population statistics [cited 2016 Jun 26]. http://www1.nyc.gov/site/planning/data-maps/nyc-population/current-future-populations.page
- The physics fact book, area of New York City [cited 2016 Jun 26]. http://hypertextbook.com/facts/2002/JordanLevine1.shtml
- New York City Center for Economic Opportunity. Poverty by borough [cited 2016 Jun 26]. http://www.nyc.gov/html/ceo/html/poverty/lookup.shtml
- New York City Department of Health and Mental Hygiene Community Health Survey [cited 2016 Jul 3]. https://a816-healthpsi.nyc.gov/epiquery/CHS/CHSXIndex.html
- HIV Epidemiology and Field Services Program. HIV surveillance annual report, 2014. New York: New York City Department of Health and Mental Hygiene; 2015.
- Weiss D, Boyd C, Rakeman JL, Greene SK, Fitzhenry R, McProud T, et al.; South Bronx Legionnaires’ Disease Investigation Team. A large community outbreak of Legionnaires’ disease associated with a cooling tower in New York City, 2015. Public Health Rep. 2017;132:241–50.
- Ricketts KD, Joseph C, Lee J, Wewalka G; European Working Group for Legionella Infections. Survey on legislation regarding wet cooling systems in European countries. Euro Surveill. 2008;13:18982.
- American Society of Heating. Refrigeration, and Air-conditioning Engineers, Inc. ANSI/ASHRAE Standard 1988–2015. Legionellosis: risk management for building water systems associated [cited 2016 Jun 26]. https://www.ashrae.org/resources–publications/bookstore/ansi-ashrae-standard-188-2015-legionellosis-risk-management-for-building-water-systems
- Cooling Technology Institute. Legionellosis guideline: best practices for control of Legionella 2008 [cited 2016 Jun 26]. http://www.cti.org/downloads/WTP-148.pdf
TablesCite This Article
1These authors contributed equally to this article.
2Current affiliation: Vital Strategies, New York, New York, USA.
- Page created: October 12, 2017
- Page last updated: October 12, 2017
- Page last reviewed: October 12, 2017
- Centers for Disease Control and Prevention,
National Center for Emerging and Zoonotic Infectious Diseases (NCEZID)
Office of the Director (OD)